Please Note: Paragraph 39 of the Settlement Agreement requires that within three months of the effective date of this Agreement, the City provide signage as necessary to comply with 28 C.F.R. § 35.163(b), after having surveyed all facilities that are the subject of this Agreement for the purpose of identifying those that have multiple entrances not all of which are accessible.
The chart below lists the facilities surveyed by the Department, the access issues identified during the survey, and the actions required to correct the access issues.
In order to ensure that the following spaces and elements in the City’s facilities in which alterations occurred after January 26, 1992, are readily accessible to and usable by persons with disabilities, the City has already taken the necessary actions.
|1.||City of Sierra Vista City Hall Building, located at 1011 North Coronado Drive.|
|1.1.||Parking: The designated van accessible space in the West parking lot is inaccessible because it lacks a van accessible sign.||Completed|
|1.2.||First Floor Main Reception Area Men’s Restroom:|
|1.2.a.||The lavatory is inaccessible because the control hardware is round and requires twisting to operate.||Completed|
|1.2.b.||The designated accessible urinal is inaccessible because the rim is not 17 inches or less above the finished floor and does not have clear floor space of at least 30 inches by 48 Inches.||Completed|
|1.3.||First Floor Main Reception Area Women’s Restroom:|
|1.3.a.||The lavatory is inaccessible because the control hardware is round and requires twisting to operate.||Completed|
|1.4.a.||The elevator is inaccessible because the hall call buttons are not raised or flush.||Completed|
|1.4.b.||The elevator is inaccessible because it does not emit a visual and audible signal indicating when the car is answering a call.||Completed|
|1.4.c.||The elevator is inaccessible because the hoistway entrance lacks raised and Braille floor designations.||Completed|
|1.5.||City Council Chambers:|
|1.5.a. (1).||The toilet paper dispenser is inaccessible because the receptacle is 50 inches above the finished floor.||Completed|
|1.5.a. (2).||The signage designating the restroom as accessible is mounted on the entry door and not the wall adjacent to the latch side of the door.||Completed|
|1.6.||Information Rack (Water Conservation): The information rack is inaccessible because at its highest point it is 64 inches above the finished floor.||Completed|
|2.0.||Ethel Burger Community Center, located at 2950 East Tacoma Street.|
|2.1.||Parking: The designated van accessible parking space is inaccessible because it lacks a van accessible sign.||Completed|
|3.0.||Fire Station Number 261, located at 1295 East Fry Boulevard.|
|3.1.a.||The designated van accessible parking space is inaccessible because it lacks a van accessible sign.||Completed|
|3.1.b.||The designated accessible parking is inaccessible because the vertical sign is mounted too low.||Completed|
|3.1.c.||The designated accessible parking is inaccessible because the built up curb ramp extends into the parking space.||Completed|